Analisa Perencanaan Penangkal Petir Pada Gedung Kampus Bima Sakti IST Akprind Yogyakarta
A natural phenomenon such as Lightning that occurs when the upper atmosphere is unstable due to the convergence of a column of warm vertical air, with a cooler mass of air above which is heated by the sun, this rising air current carries water vapor which, while filling cold air , usually condenses, causing convective storm activity, this lightning can be one of the natural causes of injury to humans or damage to electrical equipment. In planning the installation of lightning rods in the Bima Sakti IST Akprind Yogyakarta campus building using KURN R80 type with electrostatic lightning rods. For the cable carrying from the end to the control tub using the NYA cable while for grounding cable using BC cable that is connected to the ground root with a type of ground root stem which has a length of 1.5 m and a diameter of 1.5 cm. From the results of the soil resistance test, get a calculated result of 4,95 Ω, and calculated using a measuring instrument to get a result of 1.16 Ω. With the nonconventional space method in IST Akprind Yogyakarta campus building 3, the total building height up to the 27 meter final is obtained 130.4 m strike distance and 52.46 ° protection angle with a 79.45 m protection radius.
Anonim., 2011. Peraturan Umum Instalasi Penangkal Petir (PUIPP) Untuk Bangunan Indonesia. Jakarta: Direktorat Penyelidikan Masalah Bangunan.
Aris, S. 2017, Perancangan Instalasi Penangkal Petir Eksternal Metoda Franklin Pada Politeknik Enjinering Indorama, Jurnal Sinergi Vol. 21, No. 3, Oktober 2017:219-230
Dadan, A. H. (2010). Optimalisasi Sistem Penangkal Petir Eksternal Menggunakan Jenis Early Streamer (Studi Kasus UPT LAGG BPPT). 37-42.
Kunal, P. 2013, Effect of Lightning on Building and Its Protection Measures, , International Journal of Engineering and Advanced Technology (IJEAT), Volume-2, Issue-6
Lambert R., X. A. (1999). Probability Density Function of the Lightning Crest Current at Ground Level Estimation of the Litghning Strike Incidence on Transmission Line. Budapest: International Confrence on Power System.
MOORE C. B, R. W. 2000. Lightning Rod Improvement Studies, Journal of Applied Meteorology, Volume 39
MOORE, C B, G. D. AULICH, AND WILLIAM RISON, 2003, The Case for Using Blunt-Tipped Lightning Rods as Strike Receptors, Journal of Applied Meteorology, Volume 42
Mustaqqim, Naser A & Arkam M 2016, Jurnal Teknologi (Sciences & Engineering) 78:5 (2016) 7–13
Purbomilihung,2008, Lightning buster, www.blogspot .com
Supartono,E.,Haryono T, Suharyanto, 2015. Application of Cone Protection and Rolling Sphere Method in External Lightning Protection Analysis on 214 Radar Tower. International Journal of Advances in Engineering & Technology, 475-481.
Syakur, A. d. 2006. Sistem Proteksi Penangkal Petir Pada Gedung Widya Puraya.
Tarımer İlhan, Kuca. B.2013, The Proposition to Safety of a Lightning Protection System for High Structures, TEM Journal, 2(4), pp. 309-313
Yen-Hong A. Chen , Kai-Jan Lin and Yu-Chu M. Li, 2017, Assesment to Efectivenees of the new early streamer emission lightning protection system, International journal on smart sensing and iteligent systems vol 10 no.1 march 2017
Zoro, R. (2013). External Lightning Protection System for Main Office Building in the Area with High Lightning Density. Journal Elsevier Procedia Technology 11 (2013) 1238 – 1243
Copyright (c) 2019 Prosiding Seminar Nasional Teknoka
This work is licensed under a Creative Commons Attribution-NonCommercial-ShareAlike 4.0 International License.